This monitor screen will be automatically shown, after power on.
If initialized operation, the tank information is blank, please click “Setup” button to set up System (detail operation please see relevant introduction)
If need inquire detail information of each tank, please directly click the graphic of tank.
If there no operation on screen for about 5 minutes, console will automatically enter into screen saver state, black screen but program working from time to time. The screen will light again if touched.
Choose “Valid” or “Invalid” at status, to confirm the tank selected if valid or not
Choose right oil type
Choose the tank's serial number in petrol station
Choose color to distinguish different oil type
Input tank height
Choose “Yes” or “No” to start or stop automatic leak detection function
Input maximum capacity of tank
Choose desired duration of leak detection test
Choose leak detection test grade
Input the starting time of automatic leak detection test
Choose “Included” or not at Water Flag which mean cross volume include water or not.
Please do not forget to click save after setup.
When you want to delete one tank, firstly click tank at left table, and then click “Delete”.
-- Input tank serial number, please refer to the tank configure
-- Input relevant alarm values at O HH, O H, O LL, O L, Temp H, Temp L, W H, W HH
OHH alarm indicates that the oil product is likely to overfill, stop filling right now.
OH alarm indicates that the oil product already arrive the first alarm, keep your eyes on filling.
OL alarm indicates that the fuel storage inside tank is not enough, please make purchase order
OLL alarm indicates that there not fuel inside the tank, please close the business of this tank
W HH alarm indicates to the manager of petrol station make plan to remove the water out of tank
-- Input probe ID, please ensure the right ID, each probe have sole ID which same as the manufacturing code on probe nameplate, please record before install.
-- If need to calibrate oil level and water level, please measure the oil level and water level by dip stick, input the measured value in O value and W value, console program will automatically calculate the result and display on O offset and W offset. Please note that all the unit is mm
-- Please do not forget to save above information after input.
If you want to delete one of the probes, click the relevant tank at left table, click “Delete” button is ok.
Search tank volume table:
-- Click tank number, and thenclick search button at top line, user can freely look up the relevant tank volume table Up and Down.
-- Click delete if need to delete this table.
-- If you want to amend one point of tank table, choose this point data at table, input new value,
click “Update” to save the new data,
click “Delete” to delete this point data.
If the tanks in petrol station have same specification, input one tank table, click “Copy to” and choose the desired tank number, so to easily and fast input another one tank volume table.
Input tank volume table:
-- Click the table, choose one line, and then input the height and relevant volume data. After input all the data, click “Save” to save tank volume table.
Simulate tank volume table:
-- Choose one tank by the tank No., and choose the Tank type
-- Input tank’s data like diameter, length, head 1 and head 2
-- Click “Gen” button to calculate and simulate the whole tank size, and automatically generate a new tank volume table, please “Save” after finish.
Import & Export tank volume table:
-- Choose the tank by Tank No., click “Search” to display this tank’s volume table. Insert Flash
disk on the USB port of console.
-- Click “Import” button to transmit tank volume table from flash disk to console.
-- Click “Export” button to Download the tank volume table from console to flash disk.
-- Click Save after finish.